Ultrasonic Humidifier(with Digital Humidistat) :
Supply, installation, testing and commissioning of Ultra Sonic Humidifier Made out of 1.5mm S.S-304 thick sheet welded construction Horizontal Floor standing with casters, transducers, Humidistat, complete with stainless steel tank with float valve water makeup, overflow and drain connections. The transducers shall be interlocked with float switch, supplied with humidifiers and humidistat. Ultrasonic Humidifiers shall be installed within the AHU Room & the Mist connection shall be given on the suction side of supply air fan or supply side of AHU duct.
Power Supply :
Suitable for 1Phase, 230VAC +5% regulated power supply
Electrical Control Panel For Ultrasonic Humidifier: The electrical control panel shall be mounted directly on the main frame confirming to standard specification of Indian Electricity Rules. All controls shall be factory wired & tested. The control panel shall have the following accessories of makes mentioned in makes of components section.
b)On/Off Switch with light
c)Step down transformer/Power supply unit
f)PVC insulated Copper cabling for power and control circuit.
CONTROL CABINET (PANEL) :
Controls & Accessories: The Ultrasonic Humidifier will be provided and not limited to following controls & accessories
a)Water filter membrane and Air filter assembly
b)Level switches for upper and lower water level
c)Piezo transducers with Low water level protection.
d)Float valve operated Water makeup/Fill
e)Auto Drain with Valve
f)Water Overflow connection with valve
g)Mist outlet point
h)Potential free contacts for BMS operation (Optional)